This article shows a typical S Plan wiring diagram and gives an overview of the electrical control wiring connections for a Sundial / Honeywell SPlan or Drayton Twin Zone Central Heating system.S Plan Twin Zone Central Heating Wiring Diagram
(To enlarge image click once, and then double click in new window)
Please note that this is a guide only and the terminal numbers and wiring colours of systems may vary.
S Plan or SPlan Plus are fully pumped central heating systems using individual motorized zone valves to control domestic hot water and heating.
The wiring connections of SPlan heating systems may at first appear complicated because they use more than one motorized valve. Despite this, the interconnection of the thermostats and valves is relatively straight forward compared to single valve Flow Share and Biflow (mid position) or diverter valve systems. The switching operation of each side of the system follows the same sequence of; Programmer to Thermostat to Valve. The wiring connections are made even simpler because there are no ‘HW OFF’ connections at the programmer or the thermostats.
Motorised Zone Valves
Typical Motorised Actuator Valves: 2 x Sundial / Honeywell 4043 or Drayton Twin Zone 2 Port Spring return zone valves.
The Hot Water valve (located nearest to the cylinder) energizes to open and allow flow to HW.
The Heating valve energizes to open and allow flow to CH.
Each valve de-energizes to close by spring return.
Typical Wiring Colours:
Brown- Live to motor
Grey- Permanent live feed
Orange- Feed out to Boiler/Pump
White- Not required
In addition to an actuator motor (brown wire) the 4043 motorized valve contains an auxiliary micro-switch which turns on (clicks after 18 seconds) when open. This switches the (grey) permanently live input to the output (orange) which brings on the boiler/pump.
Note- White Wire. When you come to connect an SPlan heating system you may find that some 4043 2 Port motorised valves will have a white wire. This is used when the valve is installed as part of a C Plan system. The white wire is not required for S Plan and should be made electrically safe by terminating it on its own in the wiring centre junction box.
S Plus Plan- Extra Zones
The Honeywell Sundial S Plus Plan allows for additional motorized zone valves to be installed and controlled from local room thermostats for independent control of additional zones in larger systems.
Key considerations for SPlan electrical installation wiring and connecting are:
- Overview of the system’s operation- How is it required to work in that particular installation?
- Identification of the Hot Water and Heating Valves
- Siting of the main power double pole 3 amp fused spur isolator near boiler or wiring centre junction box
- Siting of the Room Stat- away from radiators and heat sources
- Boiler over run may require additional wiring to Wiring Center
- Frost Stat protection- pipework outside or in loft
Room stats are used to enhance temperature control and energy efficiency. They should be used in addition to thermostatic radiator valves. They must be sited so as to measure an average room temperature and normally at a height of 1500 mm. Be careful not to fit them near to radiators or other sources of heat or in cold draughts.
As can be seen from the S Plan wiring diagram above, the room stat ‘calling’ opens the heating motorised valve when calling for heat (brown).
When the cylinder stat calls for heat it opens the hot water motorised valve (brown).
Cylinder Stats must be connected using heat resisting cable due to high ambient temperatures surrounding central heating plumbing and their close proximity to insulation and hot surfaces. 3 core and 4 core flexible cable should be used depending on the system requirements. Never use the earth green and yellow core as a live conductor!
Frost Thermostats are used to protect vulnerable pipe work from freezing and are best sited where they exposed to outside temperatures. The function of most Frost Stats is to cause the boiler to fire and operate a circulation pump via a direct feed when the temperature drops to a preset low level. A frost stat in a S Plan or Twin Zone installation would normally connect between the permanent ‘live’ of the system (grey) and the boiler feed connection from the valves (orange). Frost Stats don’t usually require a neutral connection.
Time control is from a 2 channel programmer for independent control of hot water and heating.
Programmable cylinder stat and room stats can also be used (hard wired or wireless options).
Many boilers may have a pump over run feature where the pump is fed from it’s own connection at the boiler control connection panel. This may involve additional wiring to a remote pump where it is not installed within the boiler casing. More info about Connecting Boilers.
Find wiring diagrams and info for C Plan, S Plan / Twin Zone, W Plan & Y Plan / Biflow Central Heating Systems and Boiler Connections with Pump over-run in the ERA- Electrician’s Resources Archive.